mobiLink is a mobile and a USB interface for HART, FOUNDATION Fieldbus and PROFIBUS PA.
The Bluetooth and battery operation enables it to be used with handheld host devices such as tablets and smartphones.
mobiLink can be used in a variety of applications since it is compatible with FDT Frame applications and other major engineering tools. Additionally, It is suited for harsh environments (approved by IECEx and EX for Zone 1).
mobiLink Power: Single USB interface for PROFIBUS PA, HART, FOUNDATION fieldbus with integrated power supply for field devices
|Supported Applications||Endress + Hauser FieldCare for HART, PROFIBUS PA and FF devices; Pactware for HART, PROFIBUS PA and FF devices; |
ProComSol DevCom for HART and FF devices
|User Interface||Controls |
|Power on/off button, Bluetooth pairing button |
FIELDBUS (Fieldbus mode), HART (HART mode), Bluetooth (Pairing/Bluetooth active), Low battery, Power on
|Interfaces and Connectors||USB||Speed: USB 2.0 Full Speed, Connector: USB Type C |
Electrical: Non intrinsically safe. Do not use inside hazardous areas. 5 V, 100 mA. Um = 253 V
|Bluetooth||Dual Mode (BT Classic and BLE), 2.4 - 2.478 GHz, Output Power: +8 dBm (maximum)|
|Fieldbus||Connection: 4 mm banana type jacks (red/black), polarity has to be observed |
Physical Layer: according to IEC 61158-2, Type 1: 31.25 Kbit/s, voltage mode
Nominal input current (Fieldbus):
10 mA in Bluetooth and regular USB mode
18 mA (with fieldbus voltage > 9,5V) for increased battery life time in USB mode (controlled by application)
Fieldbus Terminator: No built-in fieldbus terminator
|HART||Connection: 4 mm banana type jacks (red/black) |
Physical Layer: HART FSK compliant modem
|Operation in Hazardous Areas||Intrinsic Safety||EX ia IIB, Ui = 30 V or FISCO field device|
|Parameters||Isolation: 1500 VDC between USB and Fieldbus, 1500 VDC between USB and HART|
|IECEx||Ex ib [ia Gb] IIB (HW version 1.00), IIC (HW version 1.01) T4 Gb; Ex ib [ia Da] IIIC T100°C Db|
|ATEX||II 2G Ex ib [ia Ga] IIB (HW version 1.00), IIC (HW version 1.01) T4 Gb; II 2D Ex ib [ia Da] IIIC T100°C Db|
|Physical Properties||Dimensions (L x W x D)||175 mm x 74 mm x 32 mm|
|Weight||330 g (incl. Batteries)|
|Power Supply||Battery: 3 * Alkaline, IEC-LR6, nominal voltage 1,5 V |
For use in hazardous area: Energizer E91 or Duracell Procell MN1500.
With batteries of other types or manufacturers certification is void.
Fieldbus interface (Medium Attachment Unit) powered by fieldbus.
|Operating Temperature||-20°C .. +50°C|
|Storage||Store batteries in a dry place at normal room temperature.|
|Relative Humidity||< 95% rH non condensing|
|Protection Class||IP 54 (if USB port covered with cap)|
|Certifications||Ex||ATEX, IECEx, FM, PCEC, KC, EAC, PESO|
|EMC/Radio||CE, FCC, SRRC, ETA, MIC, KC, EAC, TRA|
|Scope of Delivery|
|Hardware||mobiLink, USB cable, fieldbus cable set with clips, 3 * Alkaline IEC-LRC6|
mobiLink Manager, PACTware, Communication DTM for HART, Foundation Fieldbus, PROFIBUS PA, Yokogawa Interface and FDI CommServers
|Documentation||User Guide, Quick Start Guide|
|DBA-KM-020410||mobiLink for HART applications, including accessories|
|DBA-KM-020411||mobiLink including approvals for China (without approvals for USA and Canada)|
|DBA-KM-020412||mobiLink including approvals for India (without approvals for USA and Canada)|
|LRA-KK-021973||linkPlus FF – License to activate Foundation Fieldbus|
|LRA-LL-021974||linkPlus PA – License to activate PROFIBUS PA|
|LRA-KK-020721||Licence for FF Configuration Tool ComConf (linkPlus FF license required to use this)|
|Additional products and services|
|LRA-MM-020670||DevComDroid HART – Android application for HART device communication|
|LRA-MM-020671||DevCom2000 HART – Windows application for HART device communication|
|LRA-KK-020673||DevComFF.Win – Windows application for FF device communication|
|LRA-MM-020672||DevCom.iOS HART – iOS application for HART device communication|
mobiLink – Foundation Fieldbus Device Connection
In this tutorial, you will see how to use your mobiLink interface with Foundation Fieldbus field devices, for monitoring and parameterization.
mobiLink – HART Device Connection
In this tutorial, you will see how to use your mobiLink interface with HART field devices, for monitoring and parameterization.
mobiLink – Change Foundation Fieldbus Node Addresses
In this tutorial, you will see how to use your mobiLink interface with FF field devices and modify the node addresses.
How to connect your HART field device to Yokogawa FieldMate software using Mobilink
This video is a "how to" that describes how to connect FieldMate to your HART device through Mobilink.